Ultraviolet Water Sterilizer UV Water Filter Kk-UV-12W
|FOB Price:||Get Latest Price|
|Min. Order:||48 Pieces|
|Production Capacity:||800PCS Per Day|
|Payment Terms:||L/C, T/T, Western Union|
- Model NO.: KK-UV-12W
- Operating Principle: UV
- Water Purification Efficacy: Not Straight Drink
- Descaling Function: Without Descaling Function
- Trademark: OEM
- Specification: 34*11.5*7.5cm/1pcs
- HS Code: 853949000
- Style for Purifier: Wall Mounted
- Certification: CE, RoHS, SASO
- Water Temperature: Cold, Warm & Hot
- Pipe Design Rate: Incremental
- Transport Package: Colour Box
- Origin: China
Applications: Drinking water, food processing, medical and industrial etc.
Function: Disinfect bacteria, viruses, molds and algae in water.
Consumed Power: 8W-72W
Input: 110V or 220V 50/60Hz
The Ultraviolet Disinfection System is intended for the use with visually clear water, not colored, cloudy or turbid.
¨ Ambient Water Temperature: 2-45ºC
¨ Iron: <0.3ppm (0.3mg/l)
¨ Hardness: <7gpg (120mg/l)
¨ Turbidity: <1NTU
¨ Manganese: 0.05ppm (0.05mg/l)
¨ UV Transmittance: >75%
b. Recheck the installation before plug the sterilizer into power.
c. Do not proceed to install the equipment when UV Lamp or Sleeve Tube is broken, buy one again and continue.
d. Ultraviolet Disinfection System is designed for continuous operation and frequent switching will reduce Ultraviolet radiation and service life.
e. If this unit falls into the water, turn main power off and then retrieve it. Do not attempt to use this sterilizer if it has been submerged.
f. Do not operate this unit if it has a damaged cord or plug, if it is malfunctioning or if it has been dropped or been damaged in any manner.
g. The UV system should be installed after the filter on the return line.
h. Always disconnect the water supply and completely drain the water purifier if it will be subjected to temperatures below freezing for extended periods of time.
b. UV light is not visible to human eye, but harmful to eyes and skin. Never look directly at the light tube while device is in operation. Do not remove the UV Lamp from the Reactor Chamber when applying electrical power. Wear SAFETY GOGGLES if you need to look necessary.
c. Basic safety precautions should always be followed to reduce the risk of fire, electric shock. Make sure the leakage protection switch is installed before use.
d. Please do not touch the UV lamp directly in case of burning. A pair of gloves would be better when taking off it.
a. Testing monthly or before each use.
b. Lamp replacement is recommended every 8000 hours of operation. After 8000 hours, the lamp may still light, but the UV intensity has diminished.
c. Cleaning of the quartz sleeve once 3-6 months with alcohol or a mild detergent.